Phase 1 brief was a trial for 4 out of 8 rooms to reduce air change rate and therefore energy demand while maintaining the required airflow patterns for product protection.
Phase 2 brief was to deliver air change rate reductions on all 8 rooms based on Phase 1 lessons learnt.
We initially carried out as found testing for airflow measurements, room balance, ‘as found’ airflow visualisation to ISO 14644 methodology. Our recommendations from this included:
Reduce existing air change rates and recommission and balance each filling room.
Validate new air change rates and airflow distribution using airflow visualisation to ISO 14644 methodology
Validate new cleanroom classification to ISO 14644 methodology
Identify and carry out remediation work on an additional AHU resulting in energy savings and potential future breakdown avoidance
Completed to Planned Change Control, FRS, IOQ documentation
These recommendations also reduced annual maintenance costs on fans, motors and filters and reduced noise levels with positive impact on operator working conditions.
Energy savings identified (per year)
Energy cost savings identified (per year)
Emissions reduction (per year)
EECO2 delivered the HVAC design review, recommissioned the HVAC system and carried out the validation testing to protocol.
We then delivered the additional savings on the remaining rooms based on findings and lessons learned during phase 1.
We can do this for you too. Speak to us today to find out what we can deliver for your business.